SCHEDULE 23 BREATHING APPARATUS

General
4 (a) Every breathing apparatus shall be constructed of materials having adequate mechanical strength, durability and resistance to deterioration by heat or by contact with water and such materials shall be resistant to fire and shall not allow the breathing circuit to be penetrated by smoke or chemical fumes likely to be encountered in service. The fabric used in the construction of any harness provided with such apparatus shall be resistant to shrinkage. Exposed metal parts of the apparatus, harness and fittings shall be of materials so far as practicable resistant to frictional sparking.
(b) The following equipment shall be provided for use with each set of breathing apparatus:—
(i) a fire-proof life-and-signalling-line at least 3 metres longer than is required to reach from the open deck in clean air well clear of any hatch or doorway to any part of the accommodation, service, hold or machinery spaces. The line shall be made of copper or galvanised steel wire rope having a breaking strength of at least 510 kilogrammes and shall be overlaid up to at least 32 millimetres in circumference by hemp or other covering to provide a surface which can be firmly gripped when wet;
(ii) an adjustable safety belt or harness to which such line shall be capable of being securely attached and detached by the wearer by means of a snap-hook;
(iii) means for protecting the eyes and face of the wearer against smoke;
(iv) plates of suitable non-flammable material bearing a clearly legible code of signals to be used between the wearer and his attendant, one of which shall be attached to the safety belt or harness and another attached to the free end of the life-line;
(v) (for every apparatus other than a smoke helmet) a lightweight safety helmet with lining and adjustable head-band.
(c) Every breathing apparatus shall be clearly marked with the name of the maker or vendor and the year of manufacture. Operating instructions in clear and permanent lettering shall be affixed to such apparatus.